2 On or after 1 July , this Code will be mandatory for fire safety systems required by the SOLAS Convention, as amended. Any future amendment to . 22 Jul The Safety system on chapter II-2 of SOLAS is known as Fire Safety System Code (FSS code).It includes ISC,fire fighting system,fire suit,fire. 23 Sep “Equipment” includes appliances. “FSS Code” means the International Code for Fire Safety Systems, published by the IMO. “FTP Code” means.
|Published (Last):||4 August 2017|
|PDF File Size:||3.27 Mb|
|ePub File Size:||3.79 Mb|
|Price:||Free* [*Free Regsitration Required]|
This chapter details the specification of sample extraction smoke detection systems in cargo spaces as required by chapter II-2 of the Convention. The pump shall solas ffa code brought into action automatically by the pressure drop in the system before the standing fresh water charge in the pressure tank is completely exhausted. Where a momentary loss of power would cause degradation of the system, a battery of adequate capacity shall solas ffa code provided to ensure continuous operation during changeover.
FSS Code – Wikipedia
A test valve shall be installed solas ffa code the distribution piping downstream of the foam proportioner, along with orifices which reflect the calculated pressure drop of solas ffa code system. Such means shall be to the satisfaction of the Administration. As a minimum, ducts shall be led to every second deck, including movable decks. The hydraulic capability of the system shall be confirmed by the review of hydraulic calculations, followed by a test of the system, if deemed necessary by the Administration.
It shall be provided with positive means of closure.
Ga solas ffa code naar Inhoud of Menu. Type B foam concentrates solss be supplied for the protection of crude oil, petroleum products and non-polar solvent cargoes.
No other switch shall be permitted in the solas ffa code concerned. Pressure containers shall meet the requirements of the Transportations of Dangerous Goods Regulations.
In addition, all distribution piping shall be flushed with freshwater and blown through with air to ensure that the piping is free of obstructions. Slas, independent mechanical ventilation, of the extraction type, shall be provided for such a compartment. Detectors shall be periodically tested using equipment suitable for the types of fires to which the detector is designed to respond.
Stairways and corridors with a solxs width of 1, mm and over shall have handrails on both sides. The Administration may accept systems using inert gases from ffz or more separate gas generators or other solas ffa code of any combination solas ffa code, provided that an equivalent level of safety is achieved.
The stop valve in each section shall be readily accessible in a location outside of the associated section or in cabinets within stairway enclosures. The horizontal solaa of the generators shall ensure rapid supply of foam to all parts of the protected space. The ducts shall be arranged with at least 1 m free space in front of the foam delivery ducts, unless tested with less clearance.
If the box containing the controls is to be locked, a key fode the box shall be in a break-glass-type enclosure conspicuously solas ffa code adjacent to the box. A glass gauge shall be provided to indicate the correct level of the water in the tank. Relaties 3 relaties gevonden solas ffa code document.
The lifeline shall successfully pass an approval test by statical load of 3.
In case the system is out of order, procedures shall be in place to continue to monitor solas ffa code atmosphere with portable instruments solas ffa code to record the measurement results. The audible alarm sounders on the control panel and indicating units may be manually silenced. Foam generators using outside air typically consist of nozzles enclosed within a casing that spray onto a screen. Where stop valves are fitted, they shall be provided with locking arrangements.
PART IV: SOLAS CHAPTER II-2 Construction – Fire protection, fire detection and fire extinction
solas ffa code It shall not be necessary to move the containers completely from their fixing position for this purpose. Fixed pressure water-spraying fire-extinguishing systems for cabin balconies shall be approved by the Administration based on the guidelines developed by the Organization.
Different foam concentrate types shall not be mixed in a low-expansion foam system. Occurrence of a fault condition shall initiate a visual and audible fault signal at the control panel which shall be distinct from a fire signal. Detailed instruction manuals shall be provided on board, covering aolas operations, safety solas ffa code maintenance requirements and occupational health hazards relevant to the inert gas system and its application to the cargo tank system.
The donning procedures shall be quick and easy to allow for situations where there is little time to seek safety from a hazardous atmosphere. Black or galvanized solas ffa code steel. Adjacent spaces with independent ventilation systems not separated by at least A-0 class divisions should be considered as the same space. Solas ffa code gas sampling lines shall not be made of aluminium.
A minimum of two ducts cods be installed in every space containing combustion engines, boilers, purifiers, and similar equipment. In cargo ships and on passenger ship cabin balconies the fixed fire detection and fire alarm system shall, as a minimum, have section identification solas ffa code. Chapter 01 General 1 Application 1. The valve’s location shall be clearly and permanently indicated.